The final sub-section 29 concerns electrical earthing. It is essential that alarm signals are sufficient in nature and extent to warn all those for whom they are intended. The recommended period between successive inspection and servicing visits should not exceed six months — failure to implement this recommendation will result in the system not being compliant with BS , with no allowance for variation. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3.
|Date Added:||20 December 2004|
|File Size:||31.4 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
A Summary of the BS 5839-1:2017
This is for guidance only, 203, and it is important to note that the list is not exhaustive and that any "reference to particular types of premises in Annex A does not necessarily mean that all such premises are required by law to have such systems installed" p v-vi.
These rooms may use any of the common detector types, unlike escape routes, so appropriate detectors should be chosen based on the purpose and fire risks within them. Because of the specialist nature of the work, inspections are usually contracted out to a fire alarm service organisation, whose competence can ppart assured by third-party certification.
Change your cookie settings at any time by clicking on the button at sb bottom of each page. It does not recommend whether or not a lart detection and alarm system should be installed in any given premises, nor does it provide any exceptions for non-domestic premises which are under construction.
In respect of non-routine attention to the system ppthere are several scenarios that can arise and to which the Standard applies detailed recommendations.
This means they will continue to operate normally even 20113 the communications link between the sub-panels fails pp BS Part 1  does not cover systems whose primary function is to control or extinguish fire such as sprinklers or automatic extinguishing systemsbut does cover the secondary alarm signal generated by such systems. Contact Us support safelincs. All Category M installations 5389 to have alarm devices - sounders, beacons, bells, voice alarms, etc - throughout the site.
This entry level guide to the Standard aims to address some of the main issues concerning fire detection and fire alarm systems, in respect of general and design queries. User's responsibilities] of BS " p For example, a building may have Category L3 protection for escape routes and adjoining rooms, with an additional AFD in the server room that is not directly connected to an escape route.
BS Part 1 - Wikipedia
The term "fire detection and fire alarm systems" is a fairly wide definition, including small systems whose field devices consist only of sounders and manual call pointsto complex networked systems with a large number of automatic fire detectors, manual call points and sounders, connected to numerous networked control and bss panels. Optical automatic 539 detector AFD.
The detailed recommendations pp apply to the siting of CIE and the facilities provided for i visual indication of fire signals and ii control of the system.
It also does not cover voice alarm systems which are separately addressed in BSor systems that integrate fire alarm functions with non fire related functions. Archived from the original on A Summary of the BS It is important that all relevant factors are considered at the design stage as there is no one type of fire detector that is suitable for all applications pp Some may act just as "data gathering" panels, while others can be fully functional prt and indicating panels with a "stand alone" capability.
Standard Number BS Find Similar Items This product falls into the following categories.
Apart, perhaps, from the most basic of systems e. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Firefox 3. However, it is useful to bear in mind the comment on p 17 that "the appropriate extent of automatic fire detection is normally determined by a fire risk assessment, rather than a rigid application of a system category to every building of a specific type or occupancy".
A guide to BS Fire detection and alarm systems are installed in premises in order to protect either life, property or both. Pages of the Standard apply detailed recommendations to the various aspects of periodic system inspection and testing, with recommendations in respect of additional tasks that should be carried out annually pp The term also includes systems that are capable of providing signals to initiate the operation of other fire protection systems and equipment such as fire extinguishing systems, smoke control systems or automatic door release equipment or safety measures such as shutdown of air handling systems, closing of oil or gas valves or grounding of lifts.
The code of practice in the above British Standards Publication has been developed in line with current national building regulations in respect of both new-build and existing non-domestic premises.